Find great deals for Gamewell Flex If LCD Display With CPU Fire Alarm Board ASSY If Shop with confidence on eBay!. The Gamewell Retrofit Kits offered by Gamewell-FCI provide a simple way to convert without replacing the existing Gamewell backbox. IF panel. Gamewell IdentiFlex Fire Alarm Control Panel. FIRE ALARM AND SMOKE DETECTION SYSTEM. 1. GENERAL. RELATED DOCUMENTS.
|Published (Last):||11 March 2013|
|PDF File Size:||1.58 Mb|
|ePub File Size:||1.17 Mb|
|Price:||Free* [*Free Regsitration Required]|
Recently, UL updated it’s fire alarm standards from 8th edition to 9th edition. Any advice would be greatly appreciated. This way the customer has a system that is new and up to code as well as being able to purchase the apollo devices when needed. Previous topic Next topic. You cannot post new topics in this forum You cannot reply to topics in this forum You cannot edit your posts in this forum You cannot delete your posts in this forum You cannot post attachments in this forum.
The ambient temperature is fairly warm though far from hot enough to cause a legitimate alarm condition. The GW is a good panel. Would anyone happen to know if just like with the Notifier systems, that system points in the IF may just go bad??? We have literally hundreds of customers that have older gamewell systems in them.
Read times schoolguy Member Posts: The fire alarm company who was “maintaining” the system for the last ig610 years of course does gwmewell know anything about this? Yes this really happened to me ga,ewell few months ago. Anyone who tells you all their jobs are perfect is full of SH1t. It is true that the, and panels are not made any more. The GW will not show a trouble or anything system normal.
Gamewell If610 Gw31026 Y Fire Alarm Front Control Panel Display
Can anyone comfirm for me that this panel is obsolete and explain what the usual life is for heat and smoke detectors in a school. I’ve replaced the detector and now the base, but the issues continue.
This will indicate design ambient temperature of the machine room. There are replacement gamewelp available though.
If you have any Q’s let me know. Hello everyone, I’ve exhausted all of my outside resources now troubleshooting the cause of false alarms from a XPT addressable heat detector on an IF system.
Any ways the E3 will accomodate the Apollo devices and give you full control over the system ic610 even more features. January 16, Now there is ventilation provided by an exhaust fan and two open-air elctro-mechanical dampers, all of which are open and running. Most of the fire alarm builders have sunseted their older models, as a result. Most of the colleges that have a lot of Gamewell systems have a decent ammount of spare devices in stock in their maintenance iif610.
January 15, Either way I would look into the E3 as a solution for the Gamewell This works great too. Further, the rate of rise is consistent with the second tower gamdwell the property, which is not having this issue. Wed Sep 24, 6: The cost on parts for the is NOT going to go down but rather UP as parts become less and less available.
Please login or register. Heat detectors associated with elevator control should always be fixed temperature only, not ROR, in order to activate prior to the sprinkler head. I don’t know if they’re still in business as the company making the city master fire alarm boxes but the fire alarm panel line bamewell Gamewell-FCi and then got swallowed up into the Honeywell cluster. That being said, what temperature rating sprinklers are installed?
Gamewell if manual – Google Docs
Now gamewwell few years later the system gets swapped out with an E3 system and all of a sudden there is an extra address trouble on the panel. You get the picture. IF that is the case, then would anyone happen to have the software that I need to change the device address and the related functions in the program??
Not familiar with that model, gamewell chances are, he’s right. Famewell Sep 22, 5: Did you miss your activation email? That said There is a new read 2 to 3 years old panel out that you may want to look into. The Gmewell can be a direct replacement for the 6oo series GW panels. Real Knowledge From Real People. I am in charge of a large school building and am being told that my fire alarm panel is obsolete and that parts are not available. Make sure the heat detectors are rated for the same environment.
We have had no issues servicing them so far. You do not have the required permissions to view the files attached to this post. January 13, There are 2 different addressable loop cards available for it.